The Third Party Inspection for Water Tube Boiler provides a sample inspection and testing procedure during the manufacturing process. You might need to review water tube boiler inspection and test plan with this procedure.
This content covers all necessary stages in the production of the water tube boilers from the examination of the material, fabrication, welding inspection, dimensional inspection, NDE, hydrostatic testing to the final inspection, preservation and packing to despatch to the site.
You need to take this point in account this article is written for a typical Water Tube Boiler and might not be complete for special cases.
All Water Tube Boiler inspections and tests are carried out against the approved drawings, purchase order specifications, purchasers or company standards, and within the practices and rules of the country, state or province and any government decrees, laws, ordinance or regulation as may apply.
The applicable codes and specifications for the Water Tube Boiler which is under construction process are:
And the applicable codes and standards are:
The applicable codes and standard may be based other international standards such as BS 1113 and etc. This content is general and can be useful if even the design code is different from ASME Code.
Required Documents for Third Party Inspector Review:
The list of documents normally is agreed in the Pre Inspection meeting which is hold several weeks before actual commencement of inspection work. The parties which are participated in this meeting are manufacture, purchaser and third party inspection agency representatives.
This already explained in the Inspection and Test Plan for Water Tube Boiler article.
These are the list of documents which are normally agreed to be presented to the inspector:
Third Party Inspection for Water Tube Boiler - Material Inspection
The first actual inspection work in the Water Tube Boiler is raw materials inspection. Based the ASME Code providing material test reports for Water Tube Boiler plates is mandatory, for other components only the marking inspection will be enough.
But if purchase order has mandated the MTR to be provided for all components such as tubes, nozzle pipes, fittings and etc. then the manufacture need to provide them as well.
The original or authenticated copies of mill certificates for plates normally are available at manufacturer's premises. The third party inspector examines these certificates for compliance with specifications and where appropriate, drawings.
The review includes checks on:
Then the inspector witnesses the plate material identification on the certificates against plate marking. It is also necessary to check with Water Tube Boiler drawing datasheet, material list and other specification as appropriate.
The transfer identification to cut off plates also needs to be checked.
Visual inspection for surface finish and probable defects are done and dimensional compliance with specification need also to be controlled.
When the third party inspector carried out the material inspection, then provides inspection visit report, the report contains following items:
Third Party Inspection for Water Tube Boiler - Fabrication
When the Water Tube Boiler material inspection carried out and result was satisfactory or non-conformities closed by remedial action, then Water Tube Boiler manufacture will be authorised to start fabrication.
The third party Inspector checks following points on Water Tube Boiler based on the inspection and test plan (ITP) which is already agreed between purchaser and Water Tube Boiler manufacture.
The inspection scope is determined in ITP, some clients prefer to have stringent control and put the TPI inspector in more “hold points” in fabrication activities and some others may take lesser “hold points” and put TPI much more in the review document.
This depend to the inspection budget which client assign for inspection, much more inspection will have much more costs and less risks and conversely less more inspection will have less costs but more risks.
For more detail review Inspection and Test Plan for Water Tube Boiler article. There is draft ITP in this article which I believe it is the best practice for Water Tube Boiler inspection.
Third Party Inspection for Water Tube Boiler - Welded Drums and Headers Fabrications
The water tube boiler third party inspector does following inspection in mud and steam drums as well as headers:
Please note these components (Drums and Headers) in water tube boiler are similar to the pressure vessel, more detail information provided on Pressure Vessel Inspection Procedure article.
Third Party Inspection for Water Tube Boiler - Tubes and Integral Piping
The third party inspector inspects following points:
Third Party Inspection for Water Tube Boiler - Post Hydrostatic Testing
The Third party inspector makes sure:
If third party inspector is not in the hold or witness point for these stages in the project ITP, then will review water tube boiler manufacture quality control report in his/her coming visit or in final inspection day.
Third Party Inspection for Water Tube Boiler - Final Assembly
The third party inspector checks cleanliness and dryness of all components and recheck nozzles, support and bracket locations and orientations against assembly drawings.
He/she also checks for deformation of tubes, attachments, flanges, etc. and report if necessary.
Third Party Inspection for Water Tube Boiler - Name Plate Checking
The third party inspector checks the water tube boiler name plate and makes sure:
Third Party Inspection for Water Tube Boiler Painting and Coating
Surface preparation for painting is checked for the following points, according to specification by third party inspector:
Third Party Inspection for Water Tube Boiler Spares, Loose Items, Tools and Accessories:
The third party inspector controls spares, loose items, tools and accessories and make visual and dimensional inspection for materials, workmanship and quantity according to purchase order specification and packing list.
Marking and/or Tag need to be checked for identification.
Third Party Inspection for Water Tube Boiler - Reporting:
Third party inspector provides Inspection Visit Report (IVR) after each visit as well as a final report summarising the activities carried out during the boiler production in accordance with the contract requirements and circulated within the time limits specified in the contract.
The report is in the format required by the client and clearly indicates final acceptance or rejection of the water tube boiler.
Third Party Inspection for Water Tube Boiler - Release Note:
When required by the contract or purchase order a release note is issued by third party agency and given to the manufacturer when the water tube boiler have been finally accepted.
Third Party Inspection for Water Tube Boiler Packing, Marking and Shipping:
The following points is checked by the third party inspector:
The following final documents are reviewed and signed off by third party inspector:
As built, drawings if required, Manufacturer's data reports, Material certificate or certified mill test reports for all pressure parts, Material list or map, Welder record for each seam or map, Heat treatment records (Temperature-time record chart during PWHT), Dimensional record, NDE records, Production test record/mock test record, Alloy verification records, (if required), Hydrostatic test record, Pneumatic test record Hardness test record, Post weld heat treatment NDE, if specified, Name plate or other marks, Packing list, Spare parts and tool list
Third Party Inspection for Reciprocating Compressor, Third Party Inspection for Centrifugal Pump, Third Party Inspection for Gas Turbine, Third Party Inspection for Steam Turbine, Third Party Inspection for Fan and Blower, Third Party Inspection for Centrifugal Compressor, Third Party Inspection for Fire Tube Boiler, Third Party Inspection for Shell and Tube Heat Exchanger, Third Party Inspection for Fin Tube Heat Exchanger, Third Party Inspection for Pressure Vessel, Third Party Inspection for Storage Tank, Third Party Inspection for Line Pipe, Third Party Inspection for Valve, Third Party Inspection for Steel Structure, Third Party Inspection Services, Third Party Inspection Agency, Third Party Independent Inspection, Third Party Quality Inspection