This content provides you with a sample Fan Performance Test Procedure in the manufacturing vendor shop.
This article is a supplementary article for the Third Party Inspection for Fan and Blower article. Please review this article first; we will wait here for you.
This content can also be included as part of the fan factory acceptance test.
The present operative has the scope to define the operating modalities and acceptance criteria for the performance test of fan.
Performance test at inlet
Measure of pressure points on duct installed on inlet of fan;
The Quality Control operator (QC) must:
The Technical manager (TM) must:
The Quality Assurance manager (QAM) must verify the right test execution.
The test technical limits for fans running test are:
The test is performed according to ASME PTC 11 -2008 according to Volume Flow Rate – Pressure approach and the scope is to verify the contractual performance point of characteristic curve of fan.
The test is performed using n° 3, or more, different diaphragms chosen so to mach the equivalent diameter of resistant circuit.
The test media will be air. The conversion from test condition data to design ones will be performed according to AMCA 210.
Fan Performance Test - Checked Data:
Fan Performance Test - Measure To Be Done:
The test will be considered accepted if the static and total fan efficiencies are conforming to contractual range values inside the ASME PTC 11 tolerances.
Fan Performance Test - Contractual Value:
The described test shall be performed, where requested, using calibrated equipment .The instrumentation to be used consists in :
TPI Inspection for Reciprocating Compressor, TPI Inspection for Centrifugal Pump, TPI Inspection for Gas Turbine, TPI Inspection for Steam Turbine, TPI Inspection for Centrifugal Compressor, Screw Compressor Testing, Centrifugal Pump Performance Test, Centrifugal Compressor Testing, Reciprocating Compressor Testing, Fan Mechanical Running test,
Did you find this article useful? Click on below Like button!