TThe Third Party Inspection for Gas Turbine article provides a sample procedure for gas turbine inspection and gas turbine testing in the manufacturing shop. The article should be reviewed with gas turbine inspection and test paln.
This content guides you through all necessary stages in the production of the gas turbine, including the inspection of raw material to the final inspection, preservation and packing, and dispatch to site.
You need to take this point into account: this article is written for a typical gas turbine and might not be detailed for special cases.
This content may be useful for second party inspectors, gas turbine manufacturer quality control personnel, engineering companies, and purchasers, as well.
All gas turbine inspection and testing is done against the approved drawings, purchase order specifications, purchasers or company standards, and within the practices and rules of the country, state or province and any government decrees, laws, ordinance or regulation as may apply.
This content is useful primarily to open cycle combustion gas turbine units for mechanical drive operations and does not apply to the hot gas generator sets in industrial use of the aircraft pod type.
The applicable codes and specifications for a gas turbine that is under the construction process is:
and the applicable codes and standards are:
The applicable codes and standards may be based on other international standards such as JIS B8041, etc. This content is general and can be useful even if the design code is different from the API Code.
The list of documents normally is agreed upon in the Pre-Inspection meeting, which is held several weeks before the actual commencement of the inspection work.
The parties that participate in this meeting are the manufacturer, purchaser and third party inspection agency representatives.
These are the list of documents that are normally agreed upon to be presented to the inspector:
The first actual inspection work in the gas turbine is the raw materials inspection.
The original or authenticated copies of mill certificates of material normally are available at the manufacturer's premises.
The third party inspector examines these certificates for compliance with specifications, and where appropriate, drawings.
The review includes checks on:
Then the inspector witnesses the materials identification on the certificates against the materials marking. It is also necessary to check these with the gas turbine drawing datasheet, material list and other specifications as appropriate.
Visual inspection for surface finish and probable defects is done and dimensional compliance with specification need to be controlled, as well.
When third party inspector carries out the material inspection, then provides the inspection visit report (IVR), the report contains the following items:
When the gas turbine material inspection is carried out, and the results were satisfactory or non-conformities were closed by remedial action, then the gas turbine manufacturer will start fabrication.
The third party inspector checks the following points on the gas turbine based on the inspection and test plan (ITP), which has already been agreed upon between the purchaser and the gas turbine manufacturer.
The inspection scope is determined in the ITP. Some purchasers prefer to have stringent controls and assign the TPI for more “hold or witness points” for inspection and test activities, and some others prefer less “hold or witness points” and assign the TPI much more work in the “review document.”
This depends in the inspection budget, which purchasers assign for inspection. Much more inspection will have a much larger cost and less risk, and conversely, less inspection will have less cost but more risks.
The third party inspector checks the following items in the gas turbine fabrication inspection process:
The Gas Turbine and other pressure containing parts are hydrostatically tested. The main items are:
The third party inspector verifies that the correct test pressure has been applied to the relevant parts depending on specification requirements.
When required by the contract or purchase order, the third party inspector witnesses the measurement of the residual out of balance force by dynamic testing and approves the results.
When required by the contract or purchase order, the third party inspector witnesses the rotor shaft overspeed test and approves the results.
After completion of fabrication, the required clearances is checked by third party inspector in accordance with the specification requirement, the following areas are examined:
When required by the contract or purchase order, gas turbine is subjected to a mechanical running test.
Following items are taken into account for gas turbine mechanical running test:
When required by the code, contract or order, gas turbine is subjected to a governor test.
The following characteristics are considered to be important:
The third party inspector witnesses the gas turbine performance test and following points are taken in account:
After completion of all testing a visual examination including a partial strip down of the unit is usually required by the specification and is witnessed by third party inspector.
The particular areas of interest are:
The third party inspector checks the content in accordance with the approved drawings and specifications and make sure it is stamped in accordance with the code requirements.
Surface preparation for painting is checked for the following points, according to specification by third party inspector:
It is necessary that surface condition is free from pin-holes, runs damage and other discontinuity.
Spare parts, loose items and accessories are checked visually for their dimensions, materials, workmanship and quantity, according to the purchase order specification.
Test marks and tags are checked for correct identification.
The third party inspector provides an Inspection Visit Report (IVR) after each visit, as well as a final report summarizing the activities carried out during the gas turbine production in accordance with the contract requirements and circulated within the time limits specified in the contract.
The report is in the format required by the client and clearly indicates final acceptance or rejection of the gas turbine.
When required by the contract or purchase order, a release note is issued by the third party inspection agency and given to the manufacturer when the gas turbines have been accepted.
The following points are checked by the third party inspector:
The following final documents are reviewed and signed off by the third party inspector:
Manufacturer's data reports, Material certification, Dimensional record, NDE reports, Hydrostatic test reports, Rotor balance report, Clearance check report, Run-test reports, Performance test, Final inspection report, Markings, Packing list, Spare parts list
Return to Third Party Inspection
Related TPI Articles:
Reciprocating Compressor, Centrifugal Pump, Centrifugal Compressor, Steam Turbine, Fan and Blower, Screw Compressor
Did you find this article useful? Click on below Like and G+1 buttons!
New! CommentsHave your say about what you just read! Leave me a comment in the box below.