The Third Party Inspection for Fan and Blower article provides a sample procedure for fan and blower testing and fan and blower inspection in the manufacturing shop. This article needs to be reviewed with fan and blower inspection and test plan.
This content guides you through all the necessary stages in the production of the fans and blowers, including the raw material, final inspection, preservation and packing, and dispatch to site.
You need to take this point into account: this article is written for a typical fan and blower and might not be detailed for special cases.
All fan or blower inspection and testing is done against the approved drawings, purchase order specifications, purchasers or company standards, and within the practices and rules of the country, state or province and any government decrees, laws, ordinance or regulation as may apply.
The fans and blowers which are covered by this guide are four types as below:
Fans designed for air circulation are not covered by this content.
The applicable codes and specifications for Fan or Blower which is under construction process are:
The applicable codes and standard may be based any international standards. This content is general and can be useful for all applicable standards.
Required Documents for Third Party Inspector Review:
The list of documents normally is agreed upon in the Pre-Inspection meeting, which is held several weeks before the actual commencement of the inspection work. The parties that participate in this meeting are the manufacturer, purchaser and third party inspection agency representatives.
These are the list of documents that are normally agreed upon to be presented to the inspector:
The first actual inspection work in the fan or blower is the materials inspection.The original or authenticated copies of mill certificates of material normally are available at the manufacturer's premises.
The third party inspector examines these certificates for compliance with specifications, and where appropriate, drawings.
The review includes checks on:
Then the inspector witnesses the materials identification on the certificates against the materials marking. It is also necessary to check these with the fan or blower drawing datasheet, material list and other specifications as appropriate.
Visual inspection for surface finish and probable defects is done and dimensional compliance with specification need to be controlled, as well.
When the third party inspector carries out the material inspection, then provides the inspection visit report (IVR), the report contains the following items:
When the fan or blower raw material inspection is carried out, and the results were satisfactory or non-conformities were closed by remedial action, then the fan or blower manufacturer will start fabrication.
The third party inspector checks the following points on the fan or blower, based on the inspection and test plan (ITP), which has already been agreed upon between the purchaser and the fan or blower manufacturer.
The inspection scope is determined in the ITP. Some purchasers prefer to have stringent controls and assign the TPI for more “hold or witness points” for inspection and test activities, and some others prefer less “hold or witness points” and assign the TPI much more work in the “review document.”
This depends in the inspection budget, which purchasers assign for inspection. Much more inspection will have a much larger cost and less risk, and conversely, less inspection will have less cost but more risks.
Following the completion of fabrication and assembly operations the fans / blowers are inspected as required by the specification or contract and purchase order by third party inspector. The inspection consists of:
Ducting may be of rolled, welded or riveted construction depending on the service requirements. The inspector ensures that the drawing and specification requirements have been met. Particular attention is paid to site connection points.
When required by the specification ducting may be subjected to low pressure pneumatic test.
The fan and Blower unit is inspected for correct construction, rating, direction of rotation etc. to the drawing and specification requirement.
Evidence of proper impeller dynamic balance and overspeed testing are witnessed when required by the contract or purchase order.
After construction it is usual for the fan and blower unit to be subjected to a mechanical run test using the onsite driver if possible. Particular attention is paid to the following aspects of the test:
The test would be acceptable if the test result meets the specification.
The fan performance test is performed if required by the specification.
The third party inspector checks the content in accordance with the approved drawings and specifications and makes sure it is stamped in accordance with the code requirements.
Surface preparation for painting is checked for the following points, according to specification by third party inspector:
It is necessary that the surface condition is free from pin-holes, runs damage and other discontinuity.
The third party inspector controls spares, tools and accessories and make visual and dimensional inspection for materials, workmanship and quantity according to purchase order specification and packing list.
Test marks and tags are checked for correct identification.
The third party inspector provides an Inspection Visit Report (IVR) after each visit, as well as a final report summarizing the activities carried out during the fan or blower production in accordance with the contract requirements and circulated within the time limits specified in the contract.
The report is in the format required by the client and clearly indicates final acceptance or rejection of the fan or blower.
When required by the contract or purchase order, a release note is issued by the third party inspection agency and given to the manufacturer when the fans or blowers have been accepted.
The following points are checked by the third party inspector:
The following final documents are reviewed and signed off by the third party inspector in accordance to contract or purchase order requirement.
Manufacturer's data reports, Material certification, Dimensional record, NDE reports, Pressure test reports, Rotor balance report, Mechanical run test report, Final inspection report, Marking inspection report, Packing list, Spare parts list
Third Party Inspection for Reciprocating Compressor, Third Party Inspection for Centrifugal Pump, Third Party Inspection for Gas Turbine, Third Party Inspection for Steam Turbine, Third Party Inspection for Centrifugal Compressor, Third Party Inspection for Water Tube Boiler, Third Party Inspection for Fire Tube Boiler, Third Party Inspection for Shell and Tube Heat Exchanger, Third Party Inspection for Fin Tube Heat Exchanger, Third Party Inspection for Pressure Vessel, Third Party Inspection for Storage Tank, Third Party Inspection for Line Pipe, Third Party Inspection for Valve, Third Party Inspection for Steel Structure, Third Party Inspection Services, Third Party Inspection Agency, Third Party Independent Inspection, Third Party Quality Inspection
Did you find this article useful? Click on below Like and G+1 buttons!