The Third Party Inspection for Control Panel article provides a sample procedure for control panel testing and control panel inspection in the manufacturing shop. You might need to review this article with the control panel inspection and test plan.
This content guides you through all the necessary stages in the production of the control panels, including the raw material, final inspection, preservation and packing, and dispatch to site. You need to take this point into account: this article is written for a typical control panel and might not be detailed for special cases.
All control panel inspection and testing is done against the approved drawings, purchase order specifications, purchasers or company standards, and within the practices and rules of the country, state or province and any government decrees, laws, ordinance or regulation as may apply.
The applicable codes and specifications for a control panel that is under the construction process is:
The applicable codes and standards may be based any international standards. This content is general and can be useful for all recognized standards.
Required Documents for Third Party Inspector Review:
The list of documents normally is agreed upon in the Pre-Inspection meeting, which is held several weeks before the actual commencement of the inspection work. The parties that participate in this meeting are the manufacturer, purchaser and third party inspection agency representatives.
These are the list of documents that are normally agreed upon to be presented to the inspector:
The first actual inspection work in the control panel is the raw materials inspection.
The original or authenticated copies of mill certificates of material normally are available at the manufacturer's premises.
The third party inspector examines these certificates for compliance with specifications, and where appropriate, drawings.
The review includes checks on:
Then the inspector witnesses the materials identification on the certificates against the materials marking. It is also necessary to check these with the control panel drawing datasheet, material list and other specifications as appropriate.
Visual inspection for surface finish and probable defects is done and dimensional compliance with specification need to be controlled, as well.
When the third party inspector carries out the material inspection, then provides the inspection visit report (IVR), the report contains the following items:
When the control panel raw material inspection is carried out, and the results were satisfactory or non-conformities were closed by remedial action, then the control panel manufacturer will start fabrication.
The third party inspector checks the following points on the control panel, based on the inspection and test plan (ITP), which has already been agreed upon between the purchaser and the control panel manufacturer.
The inspection scope is determined in the ITP. Some purchasers prefer to have stringent controls and assign the TPI for more “hold or witness points” for inspection and test activities, and some others prefer less “hold or witness points” and assign the TPI much more work in the “review document.”
This depends in the inspection budget, which purchasers assign for inspection. Much more inspection will have a much larger cost and less risk, and conversely, less inspection will have less cost but more risks.
The third party inspector checks the following items in the control panel casing inspection process:
It is necessary the results to meet drawings and applicable standards.
The third party inspector checks that all instruments, compartments, control switches etc. are correctly rated and are correctly located, with specified labelling in accordance of approved drawings.
Insulation resistance is measured between control circuits and earth (with sensitive devises excluded) with a 500V Megger.
Similarly, insulation resistance is measured in all applicable permutations for any power circuits, if these are included within the control system, with a Megger selected to the voltage calculated appropriate to the applicable specification.
The test result depends to the circuit but would not be acceptable if it is less than 2 Megohms.
Power frequency voltage of 1.5 kV is applied between control circuits and earth for 1 minute. Similarly power frequency voltage, calculated appropriate to the applicable specification, is applied to all applicable permutations for power circuits for 1 minute.
The test would be acceptable if the no flashover and puncture occurs during the test.
Control circuitry is functionally tested and circuits proven by appropriate tests.The test result would be acceptable if meet approved schematic diagrams (including appropriate, recorded, “as built” alterations) and project philosophy
The following mechanisms are checked for operation:
The test would be acceptable if all the mechanisms work correctly.
Surface preparation for painting is checked for the following points, according to specification by third party inspector:
It is necessary surface condition to be free from pin-holes, runs damage and other discontinuity.
The third party inspector provides an Inspection Visit Report (IVR) after each visit, as well as a final report summarizing the activities carried out during the control panel production in accordance with the contract requirements and circulated within the time limits specified in the contract.
The report is in the format required by the client and clearly indicates final acceptance or rejection of the control panel.
When required by the contract or purchase order, a release note is issued by the third party inspection agency and given to the manufacturer when the control panels have been accepted.
The following points are checked by the third party inspector:
Return to Third Party Inspection
Third Party Inspection for Generator, Third Party Inspection for Bus Duct, Third Party Inspection for Power Transformer, Third Party Inspection for Power Cable, Third Party Inspection for Induction Motor, Third Party Inspection for Insulator, Third Party Inspection for Gas Circuit Breaker, Third Party Inspection for Battery Charger, Third Party Inspection for UPS Storage Battery, Third Party Inspection for Switchgear, Third Party Independent Inspection, Third Party Quality Inspection, Third Party Inspection Services, Third Party Inspection agency
Did you find this article useful? Click on below Like and G+1 buttons!