This content provide you with a draft field control system inspection and test plan. This is a draft FCS ITP and must modified based on your requirements.
|Field Control System Inspection and Test Plan Task||Vendor||TPI Inspection||Client|
|Pre-inspection meeting, when specified by Purchaser/Owner||H||H||R|
|Inventory check including the following items as minimum: 1) Inspection for general appearance including wire and cable, 2) Check that all equipment are correctly marked and located according to the layout DWGs, 3) Check that all the hardware documentation is available||H||W||R|
|Hardware system check and test including the following items as minimum: 1) Hardware system process interface input/output, 2) H1 interface and interoperability, 3) Digital inputs and outputs, 4) Analogs inputs and outputs, 5) Subsystem interface, 6) Noise immunity, radiofrequencies immuity (Note: Vendor's certificate or certificate issued by the Third Party Agent may be substituted if difficult to test), 7) Interferences between systems, 8) Functionality of redundant parts, 9) Power failure test, 10) Hardware items check and test including monitors,keybord printers etc.||H||H||R|
|Standard and application software check and test inclu. The following items as minimum: 1) Operating system test, 2) Data acquisition and control software test, 3) Application software test, 4) Communication procedure test including openness and interoperability, 5) Communication system redundancy test, 6) Powerfailure autorestart check, 7) Data logger configuration test, 8) Diagnostic function test, 9) Simulation of records||H||H||R|
|Loop configuration check and functinal test||H||W||R|
|Complex loop and logic test(including sequence and interlocks)||H||W||R|
|Control/Alarm/Trend grouping check||H||W||R|
|Communication interface test to 3rd Party Equipment,when specified||H||H||R|
|System level functional test (e.g. configuration capability, diagnostic, back-up function, etc)||H||W||R|
|System shutdown/reboot functionality check||H||W||R|
|Documentation review prior to release(Final activity of Technical Inspection)||H||H||R|
Did you find this article useful? Click on below Like and G+1 buttons!