The Third Party Inspection for Centrifugal Pump article provides a sample procedure for centrifugal pump inspection and testing in manufacturing shop and includes horizontal, vertical and in-line pumps. The article might be reviewed with centrifugal pump inspection and test plan.
This content guides you through all the necessary stages in the production of the centrifugal pumps, including the material, fabrication, casing inspection, casing hydrostatic testing, performance test, mechanical running test, net positive suction heat test, vibration test to the final inspection, preservation and packing, and dispatch to site.
You need to take this point into account: this article is written for a typical centrifugal pump and might not be detailed for special cases.
All centrifugal pump inspection and testing is done against the approved drawings, purchase order specifications, purchasers or company standards, and within the practices and rules of the country, state or province and any government decrees, laws, ordinance or regulation as may apply.
The applicable codes and specifications for a centrifugal pump that is under the construction process is:
And the applicable codes and standard are:
The applicable codes and standards may be based on other international standards such as BS 7784, etc. This content is general and can be useful even if the design code is different from the API Code.
Required Documents for Third Party Inspector Review:
The list of documents normally is agreed upon in the Pre-Inspection meeting, which is held several weeks before the actual commencement of the inspection work. The parties that participate in this meeting are the manufacturer, purchaser and third party inspection agency representatives.
These are the list of documents that are normally agreed upon to be presented to the inspector:
The first actual inspection
work in the centrifugal pump is the materials inspection. The original or
authenticated copies of mill certificates of material normally are available at the manufacturer's premises.
The third party inspector examines these certificates for compliance with specifications, and where appropriate, drawings.
The review includes checks on:
Then the inspector witnesses the materials identification on the certificates against the materials marking. It is also necessary to check these with the centrifugal pump drawing datasheet, material list and other specifications as appropriate.
Visual inspection for surface finish and probable defects is done and dimensional compliance with specification need to be controlled, as well.
When the third party inspector carries out the material inspection, then provides the inspection visit report (IVR), the report contains the following items:
Review Casing Inspection Article.
When the centrifugal pump raw material inspection is carried out, and the results were satisfactory or non-conformities were closed by remedial action, then the centrifugal pump manufacturer will start fabrication.
The third party inspector checks the following points on the centrifugal pump, based on the inspection and test plan (ITP), which has already been agreed upon between the purchaser and the centrifugal pump manufacturer.
The inspection scope is determined in the ITP. Some purchasers prefer to have stringent controls and assign the TPI for more “hold or witness points” for inspection and test activities, and some others prefer less “hold or witness points” and assign the TPI much more work in the “review document.”
This depends in the inspection budget, which purchasers assign for inspection. Much more inspection will have a much larger cost and less risk, and conversely, less inspection will have less cost but more risks.
The third party inspector checks the following items in the centrifugal pump casing inspection process:
The third party inspector checks the following items in the centrifugal pump impeller inspection process:
After complete assembly, the pump is submitted to a performance test. The test is conducted within the contract and code requirements. The third party inspector witnesses the following items:
Where required by the contract or purchase order, the third party inspector witnesses the NPSH test and approves the results.
The inspector checks the following points:
When required by the contract or purchase order, where the pump runs for a pre-determined time depending on its type, the pump and its driver will be as complete as possible. The third party inspector will check the following items:
A pump with three or more stages is inspected by dismantling after the test. Other types may be inspected when required by the contract or purchase order.
The third party inspector checks, as necessary, to ensure that no damage has occurred during tests, and that the necessary care is taken during re-assembly, including rust prevention procedures where necessary.
The establishment of running clearances is determined by giving consideration to variables such as pumping temperature, suction condition, fluid characteristics, thermal expansion or galling characteristics of the materials, etc.
The final clearances are based in accordance to the manufacturer’s standard. Where required, the third party inspector confirms that the standards have been met.
Similarly, If the third party inspector is not in the hold or witness point in the ITP for this inspection stage, then he/she will review the centrifugal pump manufacturer quality control report in his/her coming visit or on the final inspection day.
After completion of all of the manufacturing and tests, the third party inspector carries out a final inspection of the pump. Paying particular attention to:
The third party inspector checks the content in accordance with the approved drawings and specifications and makes sure it is stamped in accordance with the code requirements.
Surface preparation for painting is checked for the following points, according to specification by third party inspector:
It is necessary that the surface condition is free from pin-holes, runs damage and other discontinuity.
Spare parts, loose items and accessories are checked visually for their dimensions, materials, workmanship and quantity, according to the purchase order specification.
Test marks and tags are checked for correct identification.
The third party inspector provides an Inspection Visit Report (IVR) after each visit, as well as a final report summarizing the activities carried out during the pump production in accordance with the contract requirements and circulated within the time limits specified in the contract.
The report is in the format required by the client and clearly indicates final acceptance or rejection of the centrifugal pump.
When required by the contract or purchase order, a release note is issued by the third party inspection agency and given to the manufacturer when the pumps have been accepted.
The following points are checked by the third party inspector:
The following final documents are reviewed and signed off by the third party inspector:
Manufacturers data report, Material certification, Dimensional record, NDE reports, Hydrostatic test reports, Performance test requirements, NPSH reports, Run-test reports, Strip down reports, Final inspection report, Marking inspection report, Packing list and Spare parts list
Third Party Inspection for Reciprocating Compressor, Third Party Inspection for Centrifugal Compressor, Third Party Inspection for Gas Turbine, Third Party Inspection for Steam Turbine, Third Party Inspection for Fan and Blower, Third Party Inspection for Water Tube Boiler, Third Party Inspection for Fire Tube Boiler, Third Party Inspection for Shell and Tube Heat Exchanger, Third Party Inspection for Fin Tube Heat Exchanger, Third Party Inspection for Pressure Vessel, Third Party Inspection for Storage Tank, Third Party Inspection for Line Pipe, Third Party Inspection for Valve, Third Party Inspection for Steel Structure, Third Party Inspection Services, Third Party Inspection Agency, Third Party Independent Inspection, Third Party Quality Inspection
Did you find this article useful? Click on below Like button!